Don't let your house
go up in flames
Get it right the first time
Got Question? Get Answers
Social Media Links
Help spread our popularity, get the word
out, share us!
|Home 'Switch and Outlet Wiring Made Easy'|
Split Circuit Outlet
Read the legal disclaimer page - click the legal link in the menu at bottom of page
Split circuit outlets have been used in kitchen counter areas for use with small appliances. Codes have evolved over the years and there is some variations on codes between Canada and the United States or even between jurisdictional locations. Since I am not working in the field I want to be able to provide information about split circuits but yet refer you to our expects I have lined up in our forums for verification and specific requirements where you live.
My house was built in 1995 (in Canada) and I have split circuit outlets in the kitchen counter area and not GFI protected, having said that there has been a number of changes to the rules in regards to outlets within close distance to sinks above counter tops.
In the above picture there are two separate ungrounded conductors (hot) on a dual breaker coming to the outlet, ( the black and red wires), the single grounded conductor (neutral) gets connected at the panel to the neutral bus, there is also a equipment grounding conductor (bare wire) that gets connected to a grounding bus at the panel and to the outlet electrical box (if metallic) and to the grounding screw of outlet as well as any onward cables.
A split circuit is connected to a dual breaker at the panel, it is bridged so that is one circuit trips both circuits trip, at the outlet (or outlets) the joining tab between the brass color screws is broke off and the top half and bottom half of the outlet is on a separate circuit however a single grounded conductor (neutral) is used for the return. The two ungrounded conductors (hot) from separate circuits is connected to the brass color screws of outlet. Recent code revisions are now requiring circuits over the counter top near the sink to also have GFCI protection. Now that creates a problem with split circuits that to date I have never seen a split circuit GFI outlet. I have also read that there some variations on the type of outlet including some stating that the NEC allows to pass through 20 amps on a 15 amp outlet. Personally I prefer never to have anything that has been rated for 15 amps carry 20 amps.
Specific 20 amp outlets do come as a T shape as shown in the picture above.
I would strongly recommend that if you are wiring new kitchen outlets to take advantage of the expertise on our forums as we have moderators from both the United States and Canada on there, please be sure when seeking advice that you indicate the general area in which you live such as in the state of New York United States or live in the province of Ontario in Canada.
By: Donald Kerr
Contact Us / Creator / Legal
Copyright © 2012+
Donald Kerr / Switch and Outlet Wiring Made Easy / MegaGroup
All Rights Reserved