Don't let your house
go up in flames
Get it right the first time
Got Question? Get Answers
Social Media Links
Help spread our popularity, get the word
out, share us!
|Home 'Switch and Outlet Wiring Made Easy'|
|Fan & Light Switched Together|
|Power at Fixture [NEC 2011 compliant]|
Read the legal disclaimer page - click the legal link in the menu at bottom of page
new rule 404.2 (C) Compliant)
At the Fixture box...
At switch box...
* a) connect the red wire coming from fixture to one of
the main screws of switch.
By electrical codes you MUST have at least 6 inches of wire in the electrical box itself, and also the wire must be able to reach at least 3 inches outside the box, it can fail an electrical inspection if the required min. wire length is not met. You may have the wires a bit longer (within reason) but they cannot be shorter. Also see the note on box fill further down in this article.
Use wire nuts of the correct size to join wires together. For fan / light combination fixtures, most likely it will have wire connections, the white wire will be the grounded conductor (neutral), any green wires are equipment grounding conductors, then there will be two other wires one will be the switched ungrounded conductor (hot) for the light, and one will be the switched ungrounded conductor (hot) for the fan. If you are confused please post to our forums for further clarification.
What is not shown in the drawings to avoid confusion, is that each wire cable also has a bare equipment grounding wire included. This wire is connected to a grounding screw in each electrical box (if the box is metal), joined either through the grounding screws in the box itself or via a wire nut to the bare wire of the next cable entering / exiting the box, it is also connected to any grounding screw (if there is one) on the switch itself, as well as any grounding screw at the fixture (green wires that attach to the fixture are grounds). Now if using a plastic box, it is made of a material that is non conductive, however some plastic boxes have a metal strip inside that can still be used to connect equipment grounding wires, in the event that it does not use wire nuts to join the bare grounding wires together. The equipment grounding wire (bare in most cables) must be electrical conductively joined throughout the circuit. Green wires are also equipment grounding conductors.
If there is an equipment grounding screw on the switch it may be green in color and be separated away from the main connections of the switch and likely part of the metal frame that is also part of the mounting structure of the switch.
By: Donald Kerr
Contact Us / Creator / Legal
Copyright © 2012+
Donald Kerr / Switch and Outlet Wiring Made Easy / MegaGroup
All Rights Reserved